Need a UL508A Motor Starter for your control panel?
c3controls' Enclosed Panel Solutions are Listed per UL508A, the Standard for Industrial Control Panels.
c3controls' Enclosed Panel Solutions are Listed per UL508A, the Standard for Industrial Control Panels.
Industrial control systems are regularly under attack, yet they play a very crucial role in any manufacturing business. Unfortunately, many industrial operational technology departments have lagged in managing new threats. Starting with a robust control panel design, you can begin to better manage your business. The goal of this blog is to introduce you to these design considerations and the UL 508A Standard.Before we delve into the control panel design considerations, let’s look at some of the basics.
An industrial control panel is an assembly of standard and systematic arrangement of various components. It comprises overload relays, motor controllers, circuit breakers, and fused disconnect switches. Other related control devices include pushbutton stations, timers, switches, terminal blocks, and pilot lights, among others.According to the official definition by Underwriters Laboratories (UL), an industrial control panel is an assembly of two or more pieces of industrial control equipment. It also comes with related control circuit devices, provided with interconnecting wiring and terminals.
UL 508A certification is a directive for the industrial control panel. Electrical inspectors look for this mark as evidence of third-party certification. This is important to the municipal inspection authority and the panel purchaser.It’s a mark that shows the panel’s compliance with the acceptable safety standards. Engineers certified for the UL 508A standard advise their clients on how to design products with UL compliance. They also work with them to achieve a global design, hence eliminating the need for multiple variants.
During the installation of the panel, the NEC standards and other codes must be met. For this to happen, electrical instructions and codes must be explained on the panel. Installation can be done in one of two ways:
For the open type installation, the assembly is done in an enclosure provided by others, or at the site of installation. The enclosed type installations are done in cabinets manufactured by Purcell Systems. They must come with the UL 508A listing mark.Control panels are essential for enabling the beginning and ending procedures of a process or piece of equipment. They come in different sizes and shapes, for use in a variety of industries.
UL 508A standards commonly apply for the closed type enclosures. Benefits of choosing enclosures that carry the UL 508A certification include:
IMPORTANT: A panel that carries a UL508A certified mark does not mean that the completed control panel has been designed and tested to UL 508A standards. UL Certified only applies to the cabinet. A panel that carries the UL 508A Listed mark means that the panel, it’s electrical contents and construction meet UL 508A standards.
There are also the outdoor enclosures and cabinets whose requirements are:
These requirements are addressed in the general section of the UL requirements for all enclosures.
Industrial control panel design basics are easy to grasp. Although cost is an essential consideration, so are an attractive appearance, reliable operation, and operator controls. With simple designs, their control and maintenance are easy, and so is their production less costly.Understanding control panel designs is a crucial process that helps ensure what you want is what you get. When you first put your requirements on paper, they seem unorganized, which is acceptable. Here’s a guide to help you in making an informed decision.
A reliable control panel design comprises both electrical and physical requirements. When drawing up the schematic outlook, alternately evaluate the physical and electrical problems. This should be done until all potential issues have been eliminated.
In doing so, you minimize delivery delays and unresolved physical issues discovered during testing or production. After these considerations, drawings are created which outline the specific circuits, wiring, controls, and other aspects of the configurations.
The drawings should clearly outline:
It’s also recommended to have a clear table of contents since a proper schematic entails many different elements. This schematic lays the foundation for the process of developing the actual control panel.
Remember that the process isn’t as simple as selecting the appropriate enclosure and back panel to house the electrical hardware. Proper wiring is required, and the equipment must adequately be integrated into the machine. Improper configuration won’t only result in machinery malfunction, but will also pose an unnecessary risk to the operators.
The planning and actual construction of an industrial control panel isn’t complete without meeting the regulations.
The UL 508A control panels are designed to meet the Underwriters Laboratories (UL) standards. It gives clearance for devices that produce heat, including Variable Frequency Drives and Programmable Logic Controllers among others. The main aim is to ensure there’s enough room for ventilation.
The UL 508A certification serves to protect the quality and integrity while keeping up with the standards of public safety.
What happens if an inspector rejects a user’s control panel? The first thing is to want to understand the reason for the rejection. It could be a safety issue, or just that the equipment lacks documented adherence to the safety standards.
Your options as the client are:
In all the process, the National Electric Code is required for power wiring clearance. NEC requires a specific radius to be provided for incoming and outgoing power connections.
The installing electrician must have adequate room to make the power connections. NEC is a widely-used regulation that ensures the safe installation of electrical equipment and wiring. The regulation is adopted by states or regions to make the enforcement of safe electrical processes standardized.
According to Article 409, all industrial control panels must be examined and given a rating for their Short Circuit Current Rating (SCCR). This is established by reviewing each feeder separately then all the branch circuits. The kA value used for the whole system is the smallest one, but which must be higher than the kA value of the incoming source.
The National Fire Protection Association 79 also provides regulations for wiring standards. It’s a section of NEC that pertains to the electrical and electronic industrial machinery components. It specifically targets those operating at or below 600V.
Some types of machines under this regulation are assembly, machine tools, injection molding, and material handling machinery. Others are inspection and testing machinery. The NFPA 79 regulation safeguards machinery operators and facilities from electrical hazards and fires.
It also takes care of equipment and work-in-progress.
The environment you intend to use the control panels in largely determines the type of closure. You need a large enough space to install the components and do the wiring. It’s also a good idea to plan for several receptacles.
Doing so reduces the need for extension cords when it becomes necessary to test appliances for power.
Besides thinking about the enclosure, placement is another important consideration for control panel design. Make the necessary plans for swing requirements like cabinet doors if a cabinet will be used for closure. Factor in air conditioning and ventilation if the panel will be placed in an area with high temperature.
Where temperature control applies, plan in a way that allows for easy access to exhaust vents and air intakes. NEC requires clearance around heat producing devices to allow adequate ventilation.
One of the most common NEC violations involves control panels that are too confined or too small. Their small size doesn’t allow for wire bending and wiring. Space requirements are essential not just for the current configuration but for future adjustments.
It’s always advisable to start with the simple control components. These include timers and relays. If these don’t get the job done, go for something with more functionality.
Consider going for a Programmable Logic Controller or Smart Relay, which provide more functionality. They require a computer and programming software to achieve the desired functionality. Some manufacturers prefer to use PLCs but you should always go for the simplest control type for your application.
Just like with the control types, it’s advisable to start with simple operator devices. These include Pilot Lights, Pushbuttons, and Digital Panel Meters. To enhance the appearance, Color Graphic door laminate can be added.
For a more enhanced look and if the simple choices aren’t the best, Human Machine Interface comes in handy. It’s a color touch screen that provides more functionality. However, it also requires programming software and a computer.
Supply conductors are the elements that carry the power load. They should be able to allow for the highest possible load. This can be determined by calculating the sum of all connected apparatus and motors. Add this figure to the full load current for all resistive load plus 125% of the highest rated motor on full load current.
Overcurrent protection is another crucial consideration in control panel design phase. There are two options to hack this successfully. The first option is to place the overcurrent protection ahead of the panel. Alternatively, a primary protective device can be incorporated in the panel itself.
The second option is not very recommendable to minimize the need to open the panel’s enclosure.
The safety of the workers is of paramount importance. Manufacturers should ensure plenty of illumination and space within the panel’s enclosure. The components used should also be safe to touch, which is one of the best ways to keep workers safe.
It’s recommended to use the lowest practical voltages, usually 120Vac and 24Vdc, for automation circuits. However, some panels must have components that supply higher voltages like 480Vac power to heaters and motors.
For safety concerns, it’s highly recommended to keep voltages above 120V in separate panels and enclosures.
Excellent control panel design should make it easy for workers and operators to use an interlock. This reduces the chances that field equipment will suffer damage. It’s necessary to design fail-safe circuits so that the equipment transitions to safety when there’s power loss or disconnection.
These two components usually seem like an afterthought, but they’re equally essential to the operation of machinery. The front panels need to be durable to endure extreme weather conditions, cleaning products, and temperatures.
Faceplates and front panels may include plastic or metal substrates, depending on the specifications of the application. They can be mounted with adhesives, studs, or fasteners. Moreover, they need to have the necessary durability to remain legible throughout the life of the asset.
The importance of labeling all wires and terminals can’t be overemphasized. Despite being a time-saving strategy, it also reduces the likelihood of errors in testing, maintenance, and repairs. Labels should be able to withstand environmental conditions and must remain legible.
The UL 508A Standard refers to other UL Standards. Some of the most common ones you may need to meet are in the table below.
UL 218: Standard for Fire Pump Controllers Fire pump controllers
UL 294: Standard for Access Control System Units Control equipment for use in physical access control systems
UL 698A: Standard for Industrial Control Panels Relating to Hazardous (Classified) Locations Industrial control panels with intrinsic safety barriers intended for connection to circuits in hazardous locations
UL 845: Standard for Motor Control Centers Motor control centers
UL 864: Standard for Control Units and Accessories for Fire Alarm Systems Electrical control unit assemblies or equipment containing electrical control units for fire-protective signaling systems
UL 891: Standard for Switchboards Freestanding assemblies of circuit breakers and related applications
UL 916: Standard for Energy Management Equipment Equipment for energizing or de-energizing electrical loads to achieve the desired use of electrical power
UL 924: Standard for Emergency Lighting and Power Equipment Any equipment necessary for supplying automatic illumination and/or power to critical areas and/or equipment essential for the safety of human life
UL 1037: Standard for Antitheft Alarms and Devices Control equipment intended for theft deterrent or warning purposes
UL 1203: Standard for Explosion-Proof and Dust-Ignition-Proof Electrical Equipment for Use in Hazardous (Classified) Locations Equipment intended for use in hazardous locations
UL 1640: Standard for Portable Power-Distribution Equipment Portable control panels for specific applications
UL 1563: Standard for Electric Spas, Equipment Assemblies, and Associated Equipment Control equipment for swimming pools and spas
UL 1741: Standard for Inverters, Converters, Controllers and Interconnection System Equipment for Use With Distributed Energy Resources Equipment for controlling fuel cells, photovoltaic systems, or utility interactive systems
UL 1773: Standard for Termination Boxes Enclosures or pedestals that contain terminals for connecting power circuit conductors
UL 2017: Standard for General-Purpose Signaling Devices and Systems Covers control panels that contain emergency alarm equipment, as well as the actual alarm equipment
UL 2075: Standard for Gas and Vapor Detectors and Sensors Equipment for gas or vapor detection
UL 60950-1: Standard for Information Technology Equipment – Safety – Part 1: General Requirements Covers control panels with predominantly communication equipment
UL 508A is a control panel standard that must be met by industrial equipment. The control panel design goes a long way in determining the safety and functionality of the machinery. In the construction of control panels, there are many factors to consider.Firstly, the panels must meet safety standards and regulations stipulated by the UL and National Electrical Code. Other provisions are NFPA and CSA. Apart from meeting the regulation standards, the panels must also be well constructed for the safety of workers.
Wiring, space, controller and operator types, and enclosure must all be taken into account. If one of these factors doesn’t meet the standards, it’s highly likely that a client will need a replacement. Since control panels are a long-term investment, their design is of utmost importance.
There are many design tips and tricks that experts have developed. Do some additional research before you embark on your control panel design. The key to a successful control panel design, and passing UL inspections is to know what you are going to do before you drill that first hole!
If you’re looking for electronic control devices, be sure to browse our huge collection.
The content provided is intended solely for general information purposes and is provided with the understanding that the authors and publishers are not herein engaged in rendering engineering or other professional advice or services. The practice of engineering is driven by site-specific circumstances unique to each project. Consequently, any use of this information should be done only in consultation with a qualified and licensed professional who can take into account all relevant factors and desired outcomes. The information was posted with reasonable care and attention. However, it is possible that some information is incomplete, incorrect, or inapplicable to particular circumstances or conditions. We do not accept liability for direct or indirect losses resulting from using, relying or acting upon information in this blog post.